# GE EPM 5350 Marine Instruments User Manual

CHAPTER 9: PROGRAMMING GROUP 0 - GLOBAL METER SETUP GROUP 0, FUNCTION 6—KYZ PARAMETER SELECTION
EPM 5300 SERIES ADVANCED POWER METERS – INSTRUCTION MANUAL 9–69
Note
The unit WH refers to the counter value on the meter, where the unit equals Kilo or Mega
user-defined.
The FSW number is used only for decimal point placement (see Chapter 10).
9.8.1 How to Use KYZ Pulse Value Table for Multiplication:
Applies to -NL2 Option only:
Step 5:
a. Press VOLTS to proceed to another port (06.1 or 06.2).
Repeat this procedure to change parameters.
See Chapter 14 to Exit.
MAX/MIN
LIMITS
KVAR
PF
KW
KVA
FREQ
KWH
KVAH
AC VOLTS
AC AMPS
POWER
NC
B
A
MAX
MIN
A
N
B
N
C
N
A
B
B
C
C
A
LM2
LM1
NEXT
PHASE
VOLTS
AMPS
POWER
Table 9–2: KYZ Pulse Value
Selection
in 06P
KYZ PULSE VALUE per
Watt HOUR
FSW=9999.
KYZ PULSE VALUE per
Watt HOUR
FSW=999.9
KYZ PULSE VALUE
per Watt HOUR
FSW=99.99
KYZ PULSE VALUE per
Watt HOUR
FSW=9.999
Multiply by 1 1.0 unit WH 0.1 unit WH 0.01 unit WH 0.001 unit WH
Multiply by 2
0.5 unit WH
0.05 unit WH
0.005 unit WH 0.0005 unit WH
Multiply by 10 0.1 unit WH 0.01 unit WH 0.001 unit WH 0.0001 unit WH
Multiply by 20 0.05 unit WH 0.005 unit WH
0.0005 unit WH
0.00005 unit WH
Divide by 1 1.0 unit WH 0.1 unit WH 0.01 unit WH 0.001 unit WH
Divide by 2 2.0 unit WH 0.2 unit WH 0.02 unit WH 0.002 unit WH
Divide by 10
10.0 unit WH
1.0 unit WH
0.1 unit WH 0.01 unit WH
Divide by 20 20.0 unit WH 2.0 unit WH
0.2 unit WH
0.02 unit WH
SITUATION 1: FSW=9999.
Selection is Multiply by 2
This means that every .5 unit WH =1 pulse.
Unit=Kilo (see Group 1, Function 2)
Result: For every 1 KWH increment on the
counter, the meter will output 2 pulses.
S
ITUATION 2: FSW=999.9
Selection is Multiply by 2
This means that every .05 unit WH=1 pulse.
Unit=Kilo (see Group 1, Function 2)
Result: For every 1 KWH increment on the
counter, the meter will output 20 pulses.