  # GE EPM 5350 Marine Instruments User Manual

9–70 EPM 5300 SERIES ADVANCED POWER METERS – INSTRUCTION MANUAL
GROUP 0, FUNCTION 6—KYZ PARAMETER SELECTION CHAPTER 9: PROGRAMMING GROUP 0 - GLOBAL METER SETUP
9.8.2 How to Use KYZ Pulse Value Table for Division:
SITUATION 3: FSW=99.99
Selection is Multiply by 20
This means that every .0005 unit WH=1 pulse.
Unit=Kilo (see Group 1, Function 2)
Result: For every 1 KWH increment on the
counter, the meter will output 2,000 pulses.
S
ITUATION 4: FSW=9.999
Selection is Multiply by 20
Unit=Kilo (see Group 1, Function 2)
This means that every .00005 WH=1 pulse.
Result: For every 1 KWH increment on the
counter, the meter will output 20,000 pulses.
S
ITUATION 1: FSW=9999.
Selection is Divide by 10
This means that every 10 unit WH=1 pulse.
Unit=Kilo (see Group 1, Function 2)
Result: For every 10 KWH increment on the
counter, the meter will output 1 pulse.
S
ITUATION 2: FSW=999.9
Selection is Divide by 10
This means that every 1 unit WH=1 pulse.
Unit=Kilo (see Group 1, Function 2)
Result: For every 1 KWH increment on the
counter, the meter will output 1 pulse.
S
ITUATION 3: FSW=99.99
Selection is Divide by 20
This means that every .2 unit WH=1 pulse.
Unit=Kilo (see Group 1, Function 2)
Result: For every 1 KWH increment on the
counter, the meter will output 5 pulses.
S
ITUATION 4: FSW=9.999
Selection is Divide by 20
Unit=Kilo (see Group 1, Function 2)
This means that every .02 WH=1 pulse.
Result: For every 1 KWH increment on the
counter, the meter will output 50 pulses.